The Expansion Module connects to any EB700 Flame-Monitor Chassis by means of a ribbon cable. (P/N E350-3, E350-6).
By wiring any of sixteen interlock switches into the Expansion Module, the Flame-Monitor display automatically acts as a first-out annunciator for these interlocks. In addition, a fuel selection circuit is standard. The E300 is shipped with default messages associated with each set of terminals.
The user has the ability to modify these lockout messages in one of two ways:
1. Use the ED510 display module to select a lockout alarm message for the individual terminals of the E300 from a library of available messages.
2. Program a customized message (up to 40 characters in length) for the individual terminals of the E300 using an IBM-compatible PC with the E300 programming software and the appropriate hardware. On most P
Cs Windows Hyperterminal can be used to program E300 messages.
What Our Customers Are Saying
Thank you for having all these small crazy little parts! I can only imagine the organization of all of this! You are appreciated!
Love this website, prompt call back and had the necessary information that I was inquiring about. And had the part as well.
I found exactly what I needed to replace the compressor of my home HVAC unit, thank you for your service and I will definitely do business with your company again.
So far so good! Customer service great and site is very well laid out and easy to use. So far every part I've needed has been i stock. Thanks Voomi.
Glad I found your website. Saved a bunch of money on this order and will use again in future for my HVAC business.
By purchasing this item, you are agreeing to have this product installed by a trained technician. The installer or servicer assumes all responsibility for injury or property damage that may result. Refer to your local jurisdiction for installer licencing requirements.