Net 4 reset module. It can be used in applications that use Wiring Centers, or other zoning devices that require a single thermostat. This product provides a mounting enclosure, power for a Tekmar
Net 4 Reset Module, and connects to one Tekmar
Net 4 thermostat to control one zone pump.
Powered 115 V auxiliary pump output
Internal 56 VA transformer
Net 4 compatible
CSA C US Certified for use in USA and Canada
Agency Approvals: CSA C US, meets Class B: ICES & FCC Part 15
Ambient Conditions: Indoor use only, 32 to 122 degrees F (0 to 50 degrees C), RH less than or equal to 80 percent to 88 degrees F (31 degrees C), down to 50 percent above 104 degrees F (40 degrees C), Altitude less than 6560 ft. (2000 m), Installation Category II, Pollution Degree
Auxiliary Pump Inputs 24 V (ac) less than 0.5 VA
Auxiliary Pump Relay: 115 V (ac) 5 A
Combined Load: 11.5 A max
Control Type: Microprocessor control, this is not a safety (limit) control
Dimensions: 8-1/16 H x 11-1/8 W x 2-15/16 D (204 x 282 x 74 mm)
Enclosure Material: Blue PC+ABS plastic with metal top and bottom conduit connection walls
Enclosure NEMA Rating: NEMA 1
Power Supply: 115 V (ac) plus / minus 10 percent, 60 Hz, 12 A
Transformer Power Available: 24 V (ac) 56 VA, fuse T2.5 A 250 V
What Our Customers Are Saying
Thank you for having all these small crazy little parts! I can only imagine the organization of all of this! You are appreciated!
Love this website, prompt call back and had the necessary information that I was inquiring about. And had the part as well.
I found exactly what I needed to replace the compressor of my home HVAC unit, thank you for your service and I will definitely do business with your company again.
So far so good! Customer service great and site is very well laid out and easy to use. So far every part I've needed has been i stock. Thanks Voomi.
Glad I found your website. Saved a bunch of money on this order and will use again in future for my HVAC business.
By purchasing this item, you are agreeing to have this product installed by a trained technician. The installer or servicer assumes all responsibility for injury or property damage that may result. Refer to your local jurisdiction for installer licencing requirements.